In addition to the new Flex CHP with the TCG 2020 V20 biogas engine from MWM with 2 megawatts, electric and 2.3 megawatts, thermally, ETW also installed a combined gas storage tank with 8,490 and a heat storage tank with 1,000 cubic metres. The total investment amounts to 1.6 million euros.
Heat ensures rapid start-up
Since 2001, farmer Andreas Rohlfs has been operating a biogas plant with an area of around 235 hectares. Based on the input materials maize, dung and liquid manure, the operator generated around 5.4 million kilowatt hours of electrical energy and 4.1 million kilowatt hours of thermal energy before the expansion. Since its expansion into a storage power plant, the plant now produces 5.7 million kilowatt hours of electrical energy and almost 5.8 million kilowatt hours of heat per year. The electricity is fed into the grid; the waste heat is fed into a district heating network for heating private and municipal buildings and is used to dry wood chips. Part of the heat is diverted to keep the engine warm when it is not running. This allows the direct marketer to quickly restart the engine if necessary and immediately access the full output of the CHP.
Flex operation ensures profitability
In addition to the increase in output, the plant now operates flexibly. In return, Rohlfs will earn an additional flexibility surcharge of 40 euros per kilowatt over the next five years. Afterwards, the farmer can optionally apply for a further ten-year EEG payment by means of a tender. His main advantage: thanks to the Flex CHP, his plant is now operated in such a way that electricity and heat can always be fed in at the most productive time of day. For this purpose, the biogas plant is controlled by a direct marketer in such a way that the storage tanks are always optimally filled when prices are at their highest and that the largest possible quantities of electricity and heat are available for this purpose.
Safety alarm stops gas supply preventively
The plant is powered by desulphurised biogas. For this purpose, the sulphur content is conditioned down from around 5,000 parts per million (ppm) to around 2 ppm. A safety alarm with integrated stop of the gas supply to the storage protects the CHP at a sulphur content above 2 ppm. This is particularly necessary because the sulphur content can rise faster in flex operation. After the preventive shutdown, operation of the engine is maintained with the gas from the storage tank.
Space available for SCR catalytic converter
„In order to be prepared for future NOx limits, ETW has already reserved the necessary space on the CHP container for an SCR catalytic converter. The plans also take into account a reserve for exhaust back pressure,“ explains Alexander Szabo, the responsible sales manager at ETW Energietechnik.